This thermostat can replace a common indoor residential thermostat. It
is designed to be used with electric, gas or oil heating system. The
easy to read display shows the current room temperature and
temperature adjustment is very simple. The main advantage is that
there is no need of a cable between the thermostat and the heating
The TP-98TX should be mounted
in a dry indoor location. Choose a
mounting location about 1.5 meters
above the floor in the area with
good air circulation. Avoid places
with drafts, dead air spots and
radiant heat from the sun or
appliances. It should not be
installed close to any metal
structure or other objects that may
obstruct radio signal transmissions.
1. Remove the front housing of the thermostat. (using a screwdriver)
2. Insert the batteries. Current temperature will appear on the display if
not check the batteries.
3. Attach the thermostat to the wall with the two screws.
Mounting the receiver unit
Place the receiver unit in a suitable place near the heater. Wiring
of the unit to the heater should be done only by a professional
1. Release the upper cover by pressing the plastic log on the top side
2. Release the internal cover (1 screw).
3. Mount the unit to the desired location (2 screws).
4. Connect power 230VAC / 50Hz to terminals L and N.
5. Two PE terminals are available for a protective earth connection.
6. Terminals C (common), N.O. (normally open) and N.C. (normally
closed) are outputs of the relay contact. This contact is protected by
a 6.3A fuse. The contacts are galvanic separated.
has a unique code,
is enrolled to the
receiver unit from
A built-in LED
indicator indicates a
status of the output
In the normal operation mode the thermostat shows the room
temperature. To set a desired temperature:
1. Press or button to view the set temperature. The sign SET
will appear on the display.
or button for approximately 3 seconds till the
temperature indicator will flash once.
or button to increase or decrease the temperature
setting. If no button is pressed for 10 seconds the unit will be
switched back to the normal operation mode.
The programmed temperature range is from 5˚C to 35˚C.
The temperature span between switching ON and OFF is 1˚C. For
example, if the temperature setting is 20˚C, the heater will be switched
on when the room temperature drops to 19.5˚C and will be switched off
when the temperature rises to 20.5˚C. When the thermostat is on the
symbol HEAT will be shown on the display.
When the temperature is above 40˚C ‘HI’ will be shown on the LCD
and ‘LO’ will be shown when temperature falls below 0˚C.
When the voltage of the batteries is low the LCD will be turned off. In
that case the batteries should be changed.
Enrolment of the thermostat into the receiver unit
The thermostat has already been enrolled to the receiving unit in
the factory. If you change the thermostat for a new one it must be
enrolled to the receiver unit in the following way:
1. Remove the batteries from the thermostat for 2 minutes.
2. Remove the upper housing from the receiver unit.
3. Keep pressing the button inside the receiver until the 4th LED starts
4. Place the batteries into the thermostat. The LEDs in the receiver will
flash once to confirm the enrolment.
Note: Each receiver unit can cooperate only with one thermostat. If any
other device (remote control etc.) has been enrolled to the receiver the
receiver must be reset before enrolment of the thermostat. To reset the
memory make the 4th LED flashing by pressing the button and then
press and hold the button until all LEDs flash rapidly.
Power Source: two AAA 1.5V Alkaline batteries
Temperature Measurement: 0 - 40˚C
Temperature Accuracy: ±1.0˚C
Temperature Control: 5 - 35˚C
Temperature Control Span: 0,5˚C
Output On Delay: 20 seconds
Working frequency 433,92 MHz
Working distance up to 100 m (open area)
Coding: digital, each thermostat has a unique
Operating Temperature: -10˚C to 50˚C (non-condensing)
Storage Temperature: -30˚C to 60˚C
Size: 73.5 X 28.0 X 73.5 mm
Housing: Polycarbonate (PC)
Weight: 90 g (battery not included)
Receiver unit UC-222
Voltage: 230 V AC
Power consumption: max. 1 W
Operating frequency: 433.92 MHz
Coding: digital, each thermostat has
a unique floating code
Output relay: over switching dry contact
Fused 6 A at 250 V
Can be operated according to ERC REC 70-03
Hereby, Jablotron Ltd., declares that this TP-98is in compliance with
the essential requirements and other relevant provisions of Directive
Note: Dispose of batteries safely depending on the type of the
batteries and local regulation. Although this product does not contain
any harmful materials we suggest you to return the product to the
dealer or directly to the producer after usage.
Number of questions: 0
Do you have a question about the Joblotron TP-98 or do you need help? Ask your question here. Provide a clear and comprehensive description of the issue and your question. The more detail you provide for your issue and question, the easier it will be for other Joblotron TP-98 owners to properly answer your question.
About the Joblotron TP-98
View the manual for the Joblotron TP-98 here, for free. This manual comes under the category Thermostat and has been rated by 1 people with an average of a 9. This manual is available in the following languages: English. Do you have a question about the Joblotron TP-98 or do you need help? Ask your question here