UP Underfloor Heating ThermostatOrder No.: 0394 ..
The appliance should only be installed or fitted by a professional. The current safety regulations of the
VDE (German Electricians’ Association) and the local electricity boards must be observed during
installation. The thermostat corresponds to German norm DIN EN 60730, Type 1, and is radioscreened
in accordance with VDE 0875 and/or EN 66014.The controller works according to mode of action 1C.
1.Area of Application:
In the household forthe regulation of electrical underfloor heating systems and floor sensor systems.
2.How it Works:
The underfloor heating thermostat consists of two elements:
2.1Control device for setting the desired floor temperature.
2.2Remote sensor in the floor for monitoring the set temperature.
Use setting knob to adjust to the desired temperature. The number scale on the knob , 2, 3, 4, 5
corresponds to a temperature range of 10-50°C. Please also refer to the manufacturer’s setting
instructions for your underfloor heating. If the temperature of your floor is below that preset by you, the
control device demands heat and this state is indicated by the red LED over the setting knob. This
means that you can see when heating system is using energy.
The range can also be narrowed down by means of an adjustment to the setting knob, a more detailed
description of which is given in Item 7. The operational state of your underfloor heating system is
switched on and off by means of the mains switch. Youalso have the option of programming a
temperature reduction, for example for the night hours, by means of an external timer. If such a timer
has been installed at your home, the time when the temperature reduction is to begin is indicated by
the green LEDover the setting knob. The temperature reduction amounts to approx. 5K. Example: the
temperature you have preset at the control device is 40°C (=4 on the number scale). This means that
the temperature of the floor, for example during the night hours, can drop to 35°C without your heating
system being switched on. Your heating system would only be switched on again if the temperature
were to fall any lower.
The sensor is built into the floor. It monitors the floor temperature preset by you at the control device
and gives the command to switch the underfloor heating on and off.
UP Underfloor Heating Thermostat12/13 Page 1 of 5
Number of questions: 0
Do you have a question about the Gira 0394 or do you need help? Ask your question here. Provide a clear and comprehensive description of the issue and your question. The more detail you provide for your issue and question, the easier it will be for other Gira 0394 owners to properly answer your question.
About the Gira 0394
View the manual for the Gira 0394 here, for free. This manual comes under the category Thermostat and has been rated by 1 people with an average of a 9.7. This manual is available in the following languages: English. Do you have a question about the Gira 0394 or do you need help? Ask your question here